Greenbrook Electrical Wired In Timers
|Category:||Gardening And DIY|
|Product name:||Greenbrook Electrical Wired In Timers|
T21HA-C, T22HA-C, T23HA-C, T65A-C, T69A-C, T70A-C, T71A-C
Please note that any timer models without the letter A in the part number e.g. T21H-C are not affected. The products affected were first supplied in April 2006. All products are being removed from the supply chain.
Last year we became aware of a potential production fault with the above timers that could cause excessive heat in the terminal block and could in some cases lead to scorching and in extreme cases melting of the block and fire damage to the surrounding area.
At this time we advised that all installed timers must be checked and if necessary the terminal screws tightened. At the same time we replaced all the products held by our stockists.
Subsequently the fault has manifested itself in a small number of timers where the terminals are correctly tightened. Further forensic investigation carried out on these products has shown that the actual cause of the fault is a manufacturing defect within some terminal blocks, which did not show up in production testing.
|What to do:||
It is important therefore that all installed timers are replaced
In the meantime they should be turned off.
Do not disconnect or replace the timer unless you believe you are competent to do so.
Please contact GreenBrook Electrical on 0800 389 9446 or email email@example.com to notify us of an affected installation, to obtain a replacement if required, or to ask any questions.
Electrical Safety First recommends that anyone who discovers they have an electrical item that has been recalled should stop using it until it has been checked by the manufacturer.