11 million metres of cable recalled from the UK marketView details
- Model number
- Atlas Kablo has listed on its website batch numbers of products known to be affected at this time by the BASEC suspension and distributors are urged to inform their customers. They have a 2010 manufacturing date and are marked with the manufacturer’s identification `Atlas Kablo’.The suspension by BASEC remains in place and cables affected are: Flat twin, single and 3-core with CPC (BS 6004 Table 8 and IS 201-4 Table 1, 1.0 sqmm – 16 sqmm) Single core unsheathed (BS 6004 Table 4a, 1.5 sqmm – 35 sqmm) Single core sheathed (BS 6004 Table 7, 1.5 sqmm – 35 sqmm). Cables affected by the HAR scheme certification licence suspension have also been found to have insufficient copper leading to high conductor resistance. Cables affected are H05VV-F type, PVC insulated and sheathed in sizes ranging from 0.75 sqmm to 4.00 sqmm and with 2, 3, 4 and 5 cores.
- Recall date